Low-Level hardware hacking
In our 3 shiny new computer rooms (supercompute, IO, Tape - Each with slightly different environmental and cooling requirements), the architects have fitted a single temperature sensor on the back wall. Out of the airflow. This isn't giving us a terribly accurate picture of the supply air going into each rack, and so an alternative DIY method is underway.
A Raspberry Pi in each room (small, low enough power that it can be fed from PoE via a splitter) acts as the local 'head' and grabs the data to send it to a central message broker. From there, we can choose what to do and how to display it.
The sensor hardware consists of: A single DHT22 attached near to the Pi - As useful as these are on an arduino, on a R-Pi they are a bit harder due to the need for timing. The Adafruit interface for these grabs directly from memory address and seems well, a bit hacky. As suggested on IRC, a proper kernel module may be helpful. hint for someone else to complete :-)
The main sensor array is a set of DS18B20 sensors from fleabay (cheap if you're ordering 50 at a time) attached to the sheepwalk i2c interface 'RPI2'. These are then strung around to suit depending on location (ie, for our watercooled racks I'm going to affix the sensors directly to the flow/return lines on the watercooled racks to give us the delta-T across each set of door radiators (The BMS only gives flow/ret temp overall) which when tied to the internal temp sensors in the back of the racks should give us an idea of how well we're shifting the heat away from the machines. All this hardware comes in at less than 100 AUD per room - and some soldering time to make up the sensor chains to suit. To get an idea of the stratification (and therefore how do we position floor tiles relative to the overhead extraction vents) I'm going to put 15-20 sensors on a piece of plastic waste pipe to get a nice vertical profile - cue trip to bunnings (local DIY store) later this weekend.