Still hacking a way on MWI for Q.SIG. For some reason it's not letting me turn on/off the light at an interval quicker than ~35 seconds. It's funny, because I've been through the traces for the call, and byte-for-byte our setup message is the same as the one on a working MWI transaction. It's beginning to drive me nuts trying to identify the problem. It doesn't help very much either that the switch that I'm working against is 3000 miles away. I wonder if something's wrong in it's configuration or something. At least some how getting more information would help. Maybe I need to go out there to find out what's going on with it.